The E1 is designed to operate an aerobic treatment unit. This control panel will power one rotary or linear air compressor and one effluent pump. The E1 control will monitor the water level and system air pressure. There will be a 360 degree top mounted red light and piezoelectric buzzer in the door of the enclosure.
The 20 Amp pump circuit breaker will supply a 120VAC single phase ½ HP or smaller pump on demand. There will be a normally open pump float wired inline of the pump power that will allow the pump to run any time the float raises.
The 10 Amp air compressor circuit breaker will power one rotary or linear air compressor continuously. The 10 Amp alarm circuit breaker will power the alarm circuit. The High Water alarm is designed to be used with a normally open float switch. When the high water float switch raises the alarm light and buzzer will activate.
A standard 1 PSI pressure switch is included in the control that will monitor the system pressure. The Normally Closed contact of the switch should be used and anytime the pressure of system drops below 1 psi, the alarm light and buzzer will activate. There are alarm test and buzzer silence switches mounted in the door of the enclosure.
The enclosure has a NEMA rating of 4X which provides protection from falling dirt, falling liquids, hose-directed water and corrosive agents.
The 10”x8”x4” enclosure is made of Polycarbonate and has a hinged lockable door with latches and included screws to secure the door if required. All electrical components are mounted inside the enclosure on an aluminium back plate.